SINCO srl fits only components of new construction and the best brands. Following the assembly of the accessories is performed pressurization of the tanks to 7 bar for 24h, by controlling the endurance of the components with soapy water and the subsequent purge with inert gas (nitrogen).
For underground tanks, a turret of watertight valve protection and electrical tape has mounted, connecting the anode and electrode with subsequent execution of proof sealing of the roof unit seal. Also, the dielectric continuity with special instrumentation to 5 kv and recorded evidence on the handheld computer is checked. Where provided, the support base of reinforced concrete tanks is mounted.
Finally, the combination of tanks to the valves via barcode is performed. Progressively they proceed to INAIL testing (ex ISPSEL) with a release of the documentation supporting the matriculation book (exemption, OE approval, ten-year, valve certificate, etc.).